This study attempted to develop and suggest a more appropriate method for the determination of event mean concentration (EMC) and pollutant removal efficiency of a stormwater best management practice (BMP) considering rainfall. The stormwater runoff and hydrologic data gathered from 22 storm events during a 28-month monitoring period on a swirl and filtration type of BMP were used to evaluate the developed methods. Based on the findings, the modified EMC method resulted in lower (average) values than the overall EMC, although the differences were not significant (
>0.05). By comparison, the developed ‘Rainfall Occurrence Ratio’ (ROR) method was most significantly correlated (
=0.967 to 988,
<0.009) with the other existing removal efficiency determination methods such as the ‘Efficiency Ratio’ (ER), ‘Summation of Loads’ (SOL) and ‘Regression of Loads’ (ROL) methods. In addition, the ROR method gave the highest efficiency values, with no significant differences with any of the pollutant parameters, unlike the other three methods. These results were obtained because the ROR method integrated both pollutant loading and rainfall, which are not considered by the other three methods. Therefore, this study proved the suitability of the modified EMC and ROR methods for application in other BMP monitoring studies.
The constant expansion of water related infrastructure such as sewage treatment plants by the Korean Government has contributed to a notable reduction of point source pollution. Yet, nonpoint source (NPS) pollution is increasingly affecting water quality
. In 2003, the contribution of NPS loadings to major rivers accounted for almost half the total loading, and is predicted to rise to 70% by 2015 if no adequate control measures are introduced
. Sprawl, which is the irresponsible development,is the major contributor to the increase in NPS loadings and volume of stormwater runoff. Bannerman et al
found that streets with impervious surfaces contained the highest pollutant loads in most land use categories. Impervious covers can double, triple, quadruple or even quintuple peak discharge
. Urban stormwater managers seek technologies that are able to address the flow and water quality impacts of urbanization
The pollutant concentration-restricting approach by the Ministry of Environment (MOE) has not been very effective at improving the water quality of the major rivers in Korea. Consequently, the MOE introduced the total maximum daily load (TMDL) approach in 2004. The TMDL regulates or controls the pollution load discharged below the total amount allowed to attain the water quality target of streams
. The MOE is aggressively pursuing the implementation and compliance with the TMDL for watershed protection, and effective control of NPS is believed to be the key method for successfully meeting the TMDL
. Changes in management policies have resulted in the introduction of pilot projects, termed ‘best management practices’ (BMP), adopted from the United States. The objectives of the program are to determine catchment areas, determine runoff characteristics and evaluate the treatment performance of structural BMPs, as many introduced in Korea have only been based from literature studies that do not reflect the climatic characteristics and geographical features of the country. The results of BMP case studies will be used to facilitate the design of similar BMP types and optimize NPS management policies (e.g.,TMDL) in Korea.
Based on the National Pollutant Removal Performance Database for Stormwater Treatment Practices of the United States Environmental Protection Agency (U.S. EPA), the median performances of filtering practices for total suspended solids (TSS), total nitrogen (TN) and total phosphorus (TP) were 86, 32 and 50%, respectively
. It has to be emphasized that the median removal efficiency was used instead of the mean that resulted in higher values. The issue of reporting pollutant removal efficiencies needs to be addressed, particularly for each type of BMP, because if a wide range of removal efficiencies exists, employing an appropriate stormwater treatment strategy will be difficult. Therefore, this study aimed to develop a more appropriate method for the characterization of stormwater runoff using the event mean concentration (EMC) and calculate the pollutant removal efficiency of a stormwater runoff treatment system for BMPs. Although existing methods are available and currently practiced in most BMP studies, the uncertainties in reporting overall average EMC and removal efficiency values should be eliminated, or at least reduced. The data used in this study was obtained from a 28-month monitoring during 22 storm events on a swirl and filtration system, a type of BMP for the treatment of stormwater runoff.
2. Materials and Methods
- 2.1. Site Description and Monitoring Scheme
- 2.1.1. Site Location and Facility Description
A swirl and filtration system (surface area=19.2 m
) was installed in an asphalt-paved parking lot (100% impervious), which drained a 10,700 m
catchment area. The main function of the facility was to remove sediments, suspended solids, particulate pollutants, petroleum hydrocarbons, heavy metals and nutrients from stormwater runoff by means of sedimentation and filtration mechanisms.
shows a detailed description of the system. The facility was comprised of two devices in sequence; first, a swirl tank, which provided pre-treatment of the storm-
Schematic of the swirl and filtration system.
water runoff and was responsible for the removal of sediments, free-floating oil and debris by the mechanism of sedimentation, the runoff then flowed directly to the internal spillways across the second device, which was a filtration chamber that allowed runoff to permeate through the pores of perlite filter cartridges via filtration. Subsequently, the treated runoff was channeled through an outlet pipe and discharged to the adjacent stream.
- 2.1.2. Storm Event Sampling
A total of 22 storm events were sampled during the monitoring period from 06/2006 to 10/2008 to evaluate the pollutant removal efficiency of the swirl and filtration system in the treatment of stormwater runoff. Continuous flow measurements were performed and rainfall data collected to obtain a relatively unbiased approximation of the pollutant mass loads. The total sampling time was adjusted to approximate the time during which the “first flush” was processed
. Generally, at least 12 samples were manually collected at both the inlet and outlet. Typical water quality parameters were measured, including TSS, biochemical oxygen demand (BOD), chemical oxygen demand(COD), dissolved organic carbon (DOC), TN, TP, heavy metals (zinc, lead, etc.), and oil & grease (O&G). Analyses of these parameters were performed in accordance with standard methods
- 2.2. Calculations and Data Analyses
- 2.2.1. Event Mean Concentration
The EMC is an important factor in predicting the total pollutant load, which has made the EMC a critical parameter for estimating the contribution of runoff to receiving waters
. The EMC was used to quantify the average pollutant load washed off during a storm event with respect to the event runoff volume. The pollutant loading for a storm event is calculated by the summation of loadings during each sampling period using
the volume (or flow rate) for that period. The equation below is used for the determination of the EMC:
where EMC = event mean concentration, mg/L; V = total runoff volume per event, L; V
= runoff volume proportional to the flow rate at time i, L; C
= pollutant concentration at time
, mg/L; and
= total number of samples during a single storm event
Based on the above equation, the EMC calculated for each storm event only represents the concentration with respect to the flow or volume which might lead to overestimated or underestimated values when arithmetically averaged for the total number of storm events. For instance, a storm with little rainfall will result in a high EMC value, while that with large rainfall will yield a small EMC value because the EMC is averaged over the entire storm event. Therefore, a more specific approximation of the average EMC over the entire monitoring period was developed using the rainfall ratio, α
). The equation for the calculation of the modified EMC in this study is shown below:
= modified average EMC, mg/L; EMC
= calculated average EMC based on the rainfall range
, mg/L; α
= total rainfall depth within the rainfall range
, mm; α
= total rainfall depth,mm; and t = total number of rainfall ranges
The rainfall ranges can be selected based on the rainfall characteristics. In this study, three ranges were chosen, as follows:less than 10 mm, 10 to 20 mm and greater than 20 mm of rainfall. The EMC for each pollutant was calculated for each event and then categorized for each of the rainfall ranges. Finally, the overall EMC was computed and compared with that of the modified EMC.
- 2.2.2. Removal Efficiency
Various efficiency methods are used by investigators in BMP monitoring studies to evaluate pollutant removal efficiencies
. In this study, four methods were selected and applied to assess the efficiency of the swirl and filtration system. First, the “efficiency ratio (ER) method”
, which is defined in terms of the average removal efficiency of pollutants for each storm event (Eq. 3).
Total rainfall and number of occurrences (06/2006 to 10/2008)a)Ratio of rainfall occurrences (for each range) to total rainfall occurrences.
Total rainfall and number of occurrences (06/2006 to 10/2008) a) Ratio of rainfall occurrences (for each range) to total rainfall occurrences.
Second, the “summation of loads (SOL) method”
, which is based on the ratio of the summation of the total incoming loads to that of the total outgoing loads (Eq. 4).
Third, the “regression of loads (ROL) method”
, where the regression efficiency is defined in terms of the slope (β) of a least squares linear regression of the inlet and outlet pollutant loads, with the intercept constrained to zero (Eq. 5).
Finally, another method, termed the “rainfall occurrence ratio (ROR) method” was proposed and used in this study to evaluate the efficiency. The ROR method was developed to consider the variability of the rainfall characteristics at the monitoring site that might affect the average removal efficiency. The removal efficiency can be calculated by multiplying the average removal efficiency obtained from the ER method by the rainfall occurrence ratio, ni /nt (Eq. 6). The rainfall occurrence ratio in
equals the number of rainy days for a specific rainfall range divided by the total number of rainy days during the entire monitoring period.
All statistical hypotheses were tested at the 5% level (α = 0.05) using a one-way analysis of variance (ANOVA). The SYSTAT 12 software package (ⓒ SYSTAT Software Inc., Richmond, CA, USA,2007) and OriginPro 7.5 SRO v7.5714 (B714) (ⓒ OriginLab Corporation, Wellesley, MA, USA, 1991-2003) were used for the statistical analyses and plotting of data.
3. Results and Discussion
- 3.1. Hydrologic Data
- 3.1.1. Rainfall
The rainfall during the monitoring period between 06/2006 and 10/2008 is shown in
. A steep accumulated rainfall curve in
(a) was apparent during the summer seasons, from June to August, when most of the rainfall occurred. In Korea, a typical rainfall event averages 14 mm. However, the median rainfall is 5 mm lower than the mean which suggests most rainfall events in Korea are small. In fact, almost 68% of the rainfall that occurred
was below 10 mm, with 76% below 20 mm
(b). The sum of the maximum rainfall for each year over a three year period was about one-third of the total rainfall over three years.
provides the rainfall data used in the calculation of the modified EMC (Eq. 2) and efficiency using the ROL method(Eq. 6). Accordingly, the rainfall ratio and occurrence ratio were very different for the <10 mm and >20 mm rainfall ranges. It has to be emphasized that even though the majority of storms occurred with rainfall <10 mm, the total rainfall was still small. On the other hand, almost similar ratios were observed for the 10 to 20 mm rainfall range, indicating that this range was least affected by the modified EMC calculations.
- 3.1.2. Storm Event
The summary of the monitored event data are provided in
, which includes antecedent dry day (ADD), total rainfall,runoff duration and the sampling frequency ratio. The median rainfall was 10.5 mm, suggesting that most of the sampled storm events were less than 10 mm (50% of the total sampled events). However, the sampling ratios of each rainfall range were highly correlated (
<0.0001) with the occurrence ratio of rainfall, as shown in
, which means that the conducted sampling trips were representative of the overall rainfall in Ko-
Rainfall during the monitoring period (06/2006 to 10/2008).
Multiple hydro-and polluto graphs for the 07/09/2007 storm event.
rea during the study period. Due to the high rainfall intensity of 15.2 mm/hr during the 08/26/2006 storm (data not shown), the runoff exceeded the storage capacity of the facility and resulted in extreme overflow.
- 3.2. Runoff Water Quality
- 3.2.1. Pollutant Pattern
The plots in
illustrate the typical patterns of pollutant concentrations at the inlet and outlet of the swirl and filtration system with respect to flow and time. Apparently, the existence of the first flush was clearly identified for the TSS and metal concentrations during a relatively short period at the very beginning of the storm only at the inlet. Metals are known to often move from paved surfaces used for transportation by being adsorbed onto particulate materials
. The outlet concentration did not exhibit a first flush effect, signifying the efficiency of treatment via the swirl and filtration system. Nonetheless, the outlet concentration only appeared to be slightly reduced, and remained almost constant during the entire storm event, signifying the limitation of the swirl and filtration system in the treatment of stormwater runoff from paved areas.
Summary of the monitored event data (n=22)ADD: antecedent dry day, NA: not applicable.
Summary of the monitored event data (n=22) ADD: antecedent dry day, NA: not applicable.
- 3.2.2. Event Mean Concentration
The average pollutant concentrations of typical water quality parameters in urban runoff studies are generally quantified by means of the EMC. Given that stormwater runoff s associated with high uncertainties due to site and rainfall characteristics, the EMC values can also be affected, as reflected by the wide distribution and deviation of the EMC values found in several studies in Korea
. For example, the pollutant EMC values based on 12 stormwater runoff studies by Kim et al.
, conducted at parking lots, resulted in average EMC values of 115, 35, 4 and 1 mg/L for TSS, BOD, TN and TP, respectively. These results were higher compared to those found in this study. Climate, weather and geography tend to affect average EMC values. It is possible that a very accurate (statistical) analysis should be performed to eliminate the uncertainties in predicting EMC values.
shows the comparison of the calculated EMC values for various pollutants with respect to the three rainfall ranges (i.e., <10 mm, 10 to 20 mm and >20 mm rainfall), both cumulatively (i.e. using arithmetic average of the total events) and modified (calculated by using Eq. 2). All measured parameters exhibited significant differences between the inlet and outlet EMC values (
<0.01) for the three rainfall ranges, with the exceptions of the TSS (
=0.037) and turbidity (P=0.11). Based on the graphs, an apparent trend was observed in the relationship between the EMC and rainfall depth; the greater the rainfall, the smaller the EMC, and vice versa. Likewise, increases in the rainfall and rainfall intensity corresponded with the decrease average EMC values. Due to long duration and heavy rainfall, the average EMC value will be small. Therefore, it is safe to assume that rainfall is one of the factors affecting the differences in the EMC values, as well as the loading and flow or volume of runoff. Concurrently, rainfall can be included in the calculation of representative (overall) EMC values. Customarily, the overall EMC value is reported by arithmetically averaging the individual EMC for each storm event over the entire monitoring period. A modified EMC value was introduced in this study to account for the distribution of rainfall (termed the ‘rainfall ratio’ in
). This idea opposes the previous discussion (as depicted in
), which showed an inverse relationship between the EMC and rainfall depth. Therefore, it follows that the EMC is dependent on the rainfall ratio. Comparing the overall and modified EMC values for various pollutant parameters (
), the modified EMC values were smaller by 13±12% (mean±standard deviation) than the overall EMC values. Nevertheless, the modified EMC was highly correlated with the overall EMC, as verified by the linear fit in
- 3.3. Pollutant Removal Efficiency
The treatment capability of the swirl and filtration system was evaluated based on the total monitored storm events using four efficiency determination methods, including the ER, SOL, ROL and ROR methods. The efficiencies were also determined for each corresponding rainfall ranges. Linear correlations between the methods were displayed in the scatter plot matrix (SPLOM) in
and probability matrix in
. As revealed by the linear regression lines in SPLOM, the overall average efficiencies of the four methods were all positively correlated, with the exception of the >20 mm range. This result suggests that the efficiency of the system was highly variable when the storm event has greater than 20 mm of rainfall. Moreover, it also proves that the system is more efficient for storm events having less than 20 mm, and even better 10 mm of rainfall. The design of a facility for the treatment of stormwater runoff usually employs rainfall during which the first flush occurs because treating all, or a larger volume of runoff is impractical and uneconomical. Therefore, achieving high treatment efficiencies is still difficult (e.g. 90 to 100% pollutant removal).
Comparing the four methods, the ROR method appeared to be the most highly and significantly correlated with the other three methods, with a minimum Pearson correlation coefficient(
= 0.967 (
=0.002). The SOL method was next, and also significantly correlated with the other three methods, with a minimum
value of 0.926 (P=0.0027). On the other hand, the ER and ROL methods were not significantly correlated (P=0.343). Although the other methods are always useful to assess the overall average efficiency of the treatment system, the ROR method gave the highest confidence in reporting the overall efficiency of the treatment system. The ROR method; therefore, would be suitable for application to other BMP monitoring studies.
The overall average removal efficiency of the swirl and filtration system calculated using the four methods is shown in
. The highest removal efficiency was achieved for oil and grease (O&G) with greater than 70% removal. The other pollutant parameters merely attained less than 50% removal efficiencies. The ROF method showed the highest efficiency compared to the other three methods, with the exceptions of TSS and DOC; however, the differences were not significant. The ER method,which considers only the EMC in the calculation of the removal efficiency, yielded significantly lower efficiency value for TSS(
=0.009). In addition, the SOL and ROL methods also significantly affected the O&G removal efficiency (SOL,
=0.029). In summary, the computed removal efficiencies varied because only the EMC or mass loads of pollutant were considered.Therefore, the ROR method provided an unbiased ap-
Inlet and outlet pollutant event mean concentrations (EMC) ± standard error for each rainfall range and the cumulative EMC during the monitoring period (06/2006 to 10/2008). The modified EMC value at the inlet is denoted by the black dashed line.
Linear fit and correlation between the modified event mean concentration (EMC) and overall EMC at the inlet.
Scatter plot matrix (SPLOM) of various efficiency determination methods showing the regression line with 95% upper and lower confidence intervals using a linear smoother method; and the density in diagonal cells as displayed by the histogram.
Overall average removal efficiency of the swirl and filtration system using the four efficiency determination methods (ER SOL ROL and ROR) during the monitoring period (06/2006 to 10/2008).
Matrix of Bonferroni probabilities (P) from linear regressions on the various efficiency determination methodsER: efficiency ratio, SOL: summation of loads, ROL: regression of loads, ROR: rainfall occurrence ratio.
Matrix of Bonferroni probabilities (P) from linear regressions on the various efficiency determination methods ER: efficiency ratio, SOL: summation of loads, ROL: regression of loads, ROR: rainfall occurrence ratio.
proximation of the average removal efficiency since it takes into account both the EMC and rainfall frequency. Indeed, the rainfall characteristics govern the factors affecting the removal efficiency. For instance, for the August 26, 2006 storm event (data not shown), where the rainfall intensity was highest at 15 mm/hr (48.5 mm rainfall), overflow occurred in the sedimentation tank, which resulted in a low removal efficiency value.
The swirl and filtration system evaluated in this study is one of the many types of BMP previously and currently employed for managing stormwater runoff in Korea. However, due to variable site and climatic characteristics, it is not easy to suggest a general management strategy for the control of (NPS) pollutants in stormwater runoff. For this reason, investigations on the efficiency of treatment facilities are required. While long term monitoring of storm events is best for eliminating the uncertainties and accurately predicting the efficiency of systems, this is laborious and costly. Thus, the appropriate determination of the EMC, which is a critical and commonly used factor in estimating the pollutant removal efficiency of a treatment system, is equally important. In this study, a modified EMC calculation method and a more precise pollutant removal efficiency method (ROR) were developed, with the inclusion of rainfall as a factor. Eventually, a standard method for calculating the EMC and pollutant removal efficiency should be used for uniformity and appropriate representation of various BMPs. Based on our results, the modified EMC and ROR methods were found to be significantly correlated to the existing methods, and proven to be appropriately feasible for application. Finally, the efficiency values attained in the study of the swirl and filtration system were only satisfactory. To effectively manage stormwater runoff, both the runoff quality and quantity should be addressed. This could be achieved by restoring the water circulation lost due to excessive urbanization and by incorporating filtration and infiltration processes or through pollutant uptake by plants. Further research is still needed to investigate and improve the pollutant removal efficiencies of these BMPs.
This research was supported by the Korea Institute of Construction Technology (KICT) under the research project entitled “Development of water circulation system for urban road” (Reference No. 2010-0792). The authors are grateful to their support.
Ministry of Environment (MOE).
Water environment management master plan.
Ministry of Environment (MOE).Gwacheon: MOE; 2004.
The strategy of water control in four major rivers in Korea.
Sources of pollutants in Wisconsin stormwater.
Wat. Sci. Technol.
U.S. Environmental Protection Agency (U.S. EPA).
Handbook:urban runoff pollution prevention and control planning
Washington D.C.: U.S. EPA
Report No.: EPA 625-R-93/004.
Treatment performance of gravel filter media: implications for design and application of stormwater infiltration systems.
Characteristics of pollutants and dynamic EMCs in a parking lot and bridge during storms.
J. Korean Soc. Wat. Qual.
Soil erosion measurement and control techniques.
In: International Workshop on NewlyDeveloped Technology for Soil and Water Conservation
2005 May 31-Jun 3
National pilot projects for management of diffuse pollution in Korea.
National Pollutant Removal Performance Databasefor Stormwater Treatment Practices.
Prepared byCenter for Watershed Protection for U.S. EPA Office of Scienceand Technology
Determination of first flush criteria using dynamic EMCs (event mean concentrations) on highway stormwater runoff.
Wat. Sci. Technol.
American Public Health Association (APHA) American Water Works Association Water Environment Federation.
Standard methods for the examination of water and wastewater.
Pollution due to urban runoff: unit loads and abatement measures PLUARG.
Irish Jr. LB
Malina Jr. JF
Use of regression models for analyzing highway storm-water loads.
J. Environ. Eng.
U.S. Environmental Protection Agency (U.S. EPA)
Urbanstormwater BMP performance monitoring
WashingtonD.C.: U.S. EPA
Report No.: EPA-821-B-02-001.
U.S. Environmental Protection Agency (U.S. EPA)
Results ofthe Nationwide Urban Runoff Program. Vol. I:
Water Planning Division U.S. EnvironmentalProtection Agency
Constituent-load changes in urbanstorm water runoff routed through a detention pond-wetlandsystem in central Florida.
Tallahassee: U.S. GeologicalSurvey
Report No.: Water resources investigation
Characteristics of washoff pollutants and dynamic EMCs in parking lots and bridges during a storm.
Sci. Total Environ.
Long term monitoring of storm surface runoff from urban pavement road in Korea.
Environ. Eng. Res.